si 1220 part 2 fire-protective signaling systems control units 18 pages in hebrew 234 pages in english . revision of the mandatory standard si 1220 part 2 dealing with the control units of fire-protective signaling systems. this draft standard revision adopts the american standard st1 stockticker w stonansi st1 stockticker ul 864 - ninth edition st1 date day30 month9 w ston year2003september 30 2003 st1 date which is significantly different from the previous edition. in addition the standards hebrewsection adds the following ulli deletes the following paragraphs and their requirements 3.25-3.30 3.56 3.82 3.90 3.90.1 3.91 11.3.1 11.3.2 12.5.2sub d sub28.2 33.3.2 33.3.3 33.5 36.2.8sub g sub 36.2.10 36.2.11 36.2.12 37-49 50.2.1 50.2.3 50.2.5 50.3.1sub b sub 50.3.1sub c sub 50.4 52.6 69 78 85 89.1.1sub f sub 89.1.1sub h sub 89.1.1sub m suband 90.4sub h sub lili adds a new national remark that radio signaling is not allowed in the control units of fire-protective signaling systems in israel and therefore all the relevant paragraphs do not apply. if the use of radio signaling is approved in the future then the devices should comply with israel ministry of communications regulations lili adds a new paragraph 201 that changes the normative references lili changes paragraph 2.2 dealing with units of measurement to the metric system lili adds new remarks to paragraph 3.13 dealing with circuit classifications lili removes from paragraph 3.215 types of control unit system types lili changes the limit values of dc voltage resistors resistance and the ac current in paragraphs 3.80 3.81 lili adds 2 new paragraphs 5.201 specifies the requirements for supervisory signals or notification as non compulsory and 5.202 which requires compliance with israel standards si 961 parts 6.1 and 9.2 to prevent electromagnetic disturbances lili changes paragraph 6.4.1 lili adds a new reference to test method in paragraph 8.4 as described in israel mandatory standard si 60950 part 1 paragraph 2 lili changes the wording of the warning in paragraphs 11.2.2.4 89.1.10 and 89.1.24 lili changes the power supply range in paragraph 11.2.4.1 lili changes the cord colours in paragraph 11.2.4.3 lili prohibits the use of plugs and sockets in paragraph 11.3 dealing with cord-connected products lili adds to paragraph 12.3.1sub b 2 sub other types of cables allowed in israel lili changes the voltage range allowed in paragraphs 12.3.1 14.2 and 70.1sub b c sub lili changes the dimensions mentioned in paragraphs 12.4.2 12.4.4 12.6.2.1 and12.6.3.1 lili adds to paragraph 22.3 a requirement to mark the lam function in hebrew or by a graphic sign lili adds new international references to the requirements of paragraph 22.3 dealing with lithium batteries lili adds new national references and requirements to paragraph 24 dealing with grounding of products containing high-voltage circuits lili replaces table 30.1 dealing with test voltages lili replaces the requirements of paragraph 33.2.2 lili adds a new paragraph 34.1.201 allowing the use of audio equipmentin specific conditions and in compliance with national or international standards detailed in this paragraph lili adds a new paragraph 35.201 dealing with the requirements for fire extinguishing mechanisms or any other type of mechanism connected to the system lili changes paragraph and requires compliance with israel consumer protection order marking of goods . li ul